Propane begins to boil at minus 43.7 degrees F, at that temperature the pressure in your tank will measure zero psi. At minus 20 degrees F the tank pressure will be approximately 10.3 psi and at minus 30 degrees F 5.3 psi. Conversely at 100 degrees F the tank pressure will measure approximately 175.3 psi. The tank pressure is proportional to temperature - the gas company cannot pressurize your tank.
Typically propane furnaces will specify a gas pressure requirement at the furnace manifold. My furnace requires 10" H20 (inches of water). Since 10"H20 is equal to approximately 0.361 psi there should be sufficient pressure in your tank even at minus 30 degrees. There are likely three pressure regulators in your system, a high pressure at the tank, low pressure at the house and finally the manifold pressure on the furnace.
I would suggest the regulators be checked and adjusted as required and also have the furnace checked/cleaned as others have posted.
Fast Shipping! Most of our stocked parts ship within 24 hours (M-Th). Expedited shipping available, just call! Most prices for parts and manuals are below our competitors. Compare our super low shipping rates! We have the parts you need to repair your tractor. We are a company you can trust and have generous return policies. Shop Online Today or call our friendly sales staff toll free (800) 853-2651. [ About Us ]
TRADEMARK DISCLAIMER: Tradenames and Trademarks referred to within Yesterday's Tractor Co. products and within the Yesterday's Tractor Co. websites are the property of their respective trademark holders. None of these trademark holders are affiliated with Yesterday's Tractor Co., our products, or our website nor are we sponsored by them. John Deere and its logos are the registered trademarks of the John Deere Corporation. Agco, Agco Allis, White, Massey Ferguson and their logos are the registered trademarks of AGCO Corporation. Case, Case-IH, Farmall, International Harvester, New Holland and their logos are registered trademarks of CNH Global N.V.